|The details are regulated in the December 1998 version of the “Sample Guideline for Fireproofing-related Requirements on cavity type flooring and raised flooring” (or: “MDBR”).
Even in the countries in which this guideline has not (yet) been introduced into the building regulations, property developers can still make use of it. In developing and adopting the Sample Guideline, there will be the benefit that the representatives of the states’ building authorities will identify with its content.
Fires cannot be ruled out as a result of operating cable and duct systems, in instances, for example such as overheating. In such cases, the construction has to resist this fire load. In actual practice, it must also be noted that, with small cavities (< than 7.9” (20 cm)), due to the lack of oxygen no blazing fires can develop, which has been accordingly put into practice in the MDBR. In fire tests according to DIN 4102 and DIN EN 13 66 Part 6, ETK-stressing and loading at 1.5 kN/m. is required in Germany. For more details on this, refer to Specifications Sheet 11 of the BVS [National System Floors Association]. The MDBR is presently being revised, the details not yet having been determined at the time of printing.
When studying the MDBR, it is advisable to pay attention primarily to the text. Because most of the illustrated explanations refer to special cases, relying only on these illustrations alone may cause misunderstandings. In addition to this, one must also take into consideration the concerns of spreading fires and of partitioning in fire compartments.